On 1st September 2017 the BS 5839-1 2017 was released and has since been revised to include 25 changes to 14 existing clauses. Anyone involved in the commissioning, installation, design and planning of fire alarm and detection systems will find this standard useful.
BSI has revised BS 5839-1:2017, the Code of Practice for the design, installation, commissioning and maintenance of systems in non-domestic dwellings. The revision was published on 31st August 2017 and supersedes BS 5839-1:2013 which is now withdrawn. Some of the key changes are:
The biggest change, and the one that everyone is talking about, is the recommendation for call point covers. Going forward, all call points should be installed with a call point cover. The standard does not specify whether existing installations should be updated to include call point covers, however if an existing installation doesn’t have call point covers and the risk assessment indicates they are not required, it would be best practice to record this as a variation in the fire detection log book.
The definition of a ‘multi-sensor’ has been somewhat in dispute in recent years. Under section 3, in the Terms and Definitions, clause 3.40 defines a multi-sensor as, a “fire detector that monitors more than one physical and/ or chemical phenomenon associated with fire”. If you read on through the standard, it acknowledges that a multi-sensor could be; optical and heat, CO and heat, or smoke, heat and CO2. The standard does however accept that a multi-sensor can also be used in a single sensor state. Whichever state the multi-sensor is being used in, the detector should meet the performance requirements of the appropriate part of BS EN 54. The standard also explains that the testing of a multi-sensor can be carried out with the application of modern sensor test equipment.
Technology continues to develop at a phenomenal rate, as such, video fire detection is now a recognised specialised fire detection technique, specifically for L5 and P2 consultant specified categories.
Annexe E details the correct procedure for the selection of detector type, to reduce false alarms.
In a further attempt to reduce false alarms, Annexe E also recommends;
We hope this quick reference to the changes incorporated into BS 5839-1 2017 has been useful, however it should not be used as a substitute to the British Standard Document.
There are several other changes that have not been included in this blog, therefore please refer to BSI for full details.